The modules contain two, four-channel, thermocouple
conditioners; either four-channel conditioner can be
reassigned for use with any of the seven thermocouple
types (J, K+, S, T, B, E, or R). The low-level input signal
conditioning includes f 1OOOV DC, isolation, high
common mode rejection, filtering and low drift amplification. Signal integrity is further preserved by a highaccuracy programmable-gain amplifier and a 13-bit integrating A/D converter.
The output of this converter constitutes a 13-bit word (12
bits plus sign) equivalent to k 4096 counts of resolution.