Required equipment: Voltmeter - 5 digit
250 ohm Precision Resistor
Calibration Connector (IC600MA508A)
Small screwdriver with approximately 3 inch insulated shaft.
Calibration of the Analog Output module should be performed every 90 days. For maximum accuracy the module should be
calibrated at the normal ambient temperature which occurs in operation.
1. SET UP:
Loosen the thumbscrews, remove the faceplate, taking care that the field wiring is not disturbed. Place the calibration connector on the front edge of the module. For the 0 to + 10 V or the -10 V to + 10 V module connect a Digital
Voltmeter (DVM) between the terminals of the calibration connector as listed in the